Welcome back! You are now signed in.
You have been logged out due to inactivity
Please enter the email address you used to create the account. We'll send you a link that lets you create a new password.
Please check your email. Click the link in the email to create a new password.
The following are all the IBC Category D,E,F2 Code Requirements for lay-in acoustical panels and direct-hung acoustical tiles.
The specifications below are for standard applications.
View an alternate solution that delivers additional options.
|Basic Connections, Perimeter, and Lateral Splay Bracing||Requirements|
|Minimum intersection strength limits @ MT / CT||180 lbs|
|Vertical hanger wire 12-gauge @ 4' o.c.||Required|
|Connection device from vertical wire to the structure above must sustain min 100 lbs||Required|
|Main tee classifications||Heavy-duty|
|1 in 6 max plumb of vertical hanger wires||Required|
|Perimeter vertical hanger wires not more than 8" from wall||Required|
|Grid end/wall clearance||Min 3/4"|
|Perimeter closure (molding) width||Min 2 "|
|Grid connection to perimeter attached on two adjacent walls||Required|
|Perimeter tee ends tied together||Required|
|Horizontal restraint (splay wires or rigid bracing) within 2" of intersection and splayed 90° apart at 45° angles||Required|
|Compression posts (struts) 12' o.c. in both directions, starting 6' from walls||Required|
|Splay bracing connection strength 200 lbs or the design load, whichever is greater||Required|
|Partition attachment||Bracing independent of ceiling splay bracing|
|Seismic separation joint4||Required for areas > 2,500 sq. ft. (or full height partition)|
|Rigid bracing for ceiling plane elevation changes||Required|
|Light Fixture Attachment||Requirements|
|Light fixture (all types) mechanically attached to grid NEC 410-16 (two per fixture unless independently supported)||Required|
|- Surface-mounted fixtures attached to grid||Not required|
|- Pendant-hung fixtures directly supported from structure with 9-gauge wire (or approved alternative)||Required|
|- Rigid lay-in or can light fixtures|
|≤ 10 lbs – one wire to structure (may be slack)||Required|
|11 to 56 lbs – two wires from housing to structure (may be slack)||Required|
|≥ 57 lbs – supported directly to structure by approved||Required|
|Light Fixture Supplementary Hanger Wires||Requirements|
|Intermediate Duty Main Tees with cross tee rating below 16 lbs./LF||Required|
|- Min. 12-gauge hanger wires must be attached to the grid members within 3 inches of each corner of each light fixture.|
|Heavy Duty Main Tees with cross tee rating below 16 lbs./LF||Required|
|- Min. 12-gauge hanger wires must be attached to the supporting cross tee within 3 inches of the corner of each light fixture.|
|Supplementary hanger wires for Heavy Duty Main Tees with cross tee rating equal to 16 lbs./LF||Not Required|
|≤ 20 lbs – positively attached to grid||Required|
|21 to 56 lbs – positively attached to grid and two wires to structure (may be slack)||Required|
|≥ 57 lbs – directly supported to structure||Required|
|Sprinkler heads and other penetration clearance||Min 2" dia. opening or a swing joint|
|Cable trays and electrical conduit independently supported and braced||Required|