Please enter the email address you used to create the account. We'll send you a link that lets you create a new password.
Please check your email. Click the link in the email to create a new password.
|Physical and Mechanical Properties||Test Standard||Approximate Values Standard (Metric)|
|Noncombustibility||ASTM E136-12 (unmodified) |
|Surface-burning characteristics |
(flame spread/smoke developed)
|ASTM E84 |
|Weight (3/4in. [19mm] thickness)||ASTM D1037||5.3 lb./ft.2 (26 kg/m2)|
|Mold resistance||ASTM D3273, ASTM G21||10, 0|
|Termite resistance||AWPA Standard E1-13||9.8|
|Low VOC emissions||CDHP/EHLB/Standard Method V1.1-2010a||Compliant|
|Concentrated load||ASTM E661||550 lb. (2.45 kN) static 0.108 in. (2.7 mm) max. deflection @ 200 lb. (0.89 kN)|
|Water absorptionb||ASTM C1185, Sec. 220.127.116.11||<15.0%|
|Linear variation with change in moisture |
(25% to 90% relative humididty)
|ASTM C1185, Sec. 8||<0.10%|
(a) Reference Standard: California Department of Public Health CDPH/EHLB/Standard Method Version 1.1, 2010 (Emission testing method for CA Specification 01350).
(b) Absorption measured from equilibrium conditioning followed by immersion in water for 48 hours.